Cooling water circulation system of central air conditioning
The cooling water circulation system is a kind of central air conditioning system. It refers to the water supply system for cooling water to heat and cool down and recycle. It is mainly composed of cooling equipment, pumps and pipelines, including open and closed two types. The principle of cooling water circulation system is a cooling water system that uses water as a cooling medium and uses it circulate. It is mainly composed of cooling equipment, water pump and pipe. Need cooling cold water flowing through the production equipment (often called heat transfer equipment, such as heat exchanger, condenser, reactor), the temperature rise, if is cold water emissions, only once (called direct cooling water system), warm up the cold water flowing through the cooling water temperature equipment is reduced, can be pumped back to the production equipment used again water consumption is reduced greatly, often can save more than 95%. Cooling water accounts for about 70% of the amount of water used in industry, so the cooling water circulation system plays a role in saving a lot of industrial water.
The cooling equipment is divided into open and closed type, so the cooling water circulation system is also divided into two types: open and closed. The design and operation of the open system are more complicated.
The cooling equipment has two kinds of cooling pool and cooling tower, which mainly depend on the evaporation of water to reduce the temperature of water. Furthermore, the cooling tower is often used as a fan to promote evaporation, and the cooling water is often blown away. So open cooling water circulation system must be supplied with fresh water. Because of evaporation and concentration of circulating water, the concentration process will promote the scaling of salt. The supplemental water has a dilution effect, and the flow rate is often determined according to the limit of circulating water concentration. Usually, the amount of water is more than the loss of water from evaporation and wind, so some circulating water must be discharged to maintain the balance of water. The cooling water circulation system in the open system, because the water in contact with the air, dust and microorganisms into the circulating water; in addition, the carbon dioxide emission and material leakage for thermal equipment, water quality change of circulating water. For this reason, circulating cooling water often needs to be treated, including sediment control, corrosion control and microbial control. The determination of the treatment method is often related to the water quantity and water quality of the recharge water, and it is also related to the performance of the production equipment. When a variety of agents are used, the possible chemical reactions between the agents should be avoided.
Closed cooling water circulation system adopts closed cooling equipment, circulating water flows in pipe, and wind is usually used outside the tube. There are no other factors to change the water quality of the circulating water except for the material leakage of the heat exchange equipment. In order to prevent salt scaling in the heat exchange equipment, sometimes the cooling water needs to be softened. In order to prevent corrosion of heat exchangers, corrosion inhibitors are often added. Attention should be paid to the safety of highly concentrated and highly toxic corrosion inhibitors. The discharged cooling water should be properly disposed during maintenance.
Cooling cycle system component
The size of the media flow monitoring system in the pipeline, in the pipeline due to blockage of factors according to the pipe flow rate is too low or too high, can be issued in a timely manner to the offline control system alarm (flow rate is too low) or on-line alarm (high flow) provides the switch signal, we call flow alarm switch.
In general, the role of cooling water circulation system is to transfer the heat generated by the equipment or instrument from the liquid carrier from the device, and send the heat to the outside of the machine through the refrigerator, so as to ensure that the device works in the normal temperature range.